ERGIL Storagetech™ Flame Arrester (Vertical, in-line, detonation)
Model No: 320
ERGIL Storagetech™’s Model 320 In-line Detonation Flame Arrester (also called flame arrestor or fire arrestor) is designed for installation in gas pipelines. Detonation occurs when a flame travelling through the pipeline reaches supersonic velocities, usually as a result of the pipeline configuration or pipeline surface roughness. Changes in gas density and pressure causes the flame velocity to metamorphose from subsonic to supersonic.
The flame quenching element is designed to be three or four times the area of the pipe in which it is installed, and is assembled between two flanged reducing spools. The element comprises a tightly rolled scroll or scrolls of crimped stainless steel ribbon to form passages through which the vapour passes. The area of each passage determines level of protection that the element provides. ERGIL Storagetech™’s Model 320 In-line Detonation Flame Arrester has a maximum experimental safe gap (MESG) as per the standard, and is suitable for gas groups IIB and IIA.
The detonation flame arrestor is more robust than the deflagration flame arrester, and contiguous scrolls have smaller MESGs to withstand higher pressures and to quench detonations. It should be installed in the pipeline where there is a significant distance between the unit and the potential source of ignition.
The unit is supplied with an earth point, copper tag and cable. Temperature sensor can be provided upon request. The element can easily be removed for cleaning or replacement.
|Standard sizes||: 1” to 12” DN25 to DN300|
|Body / Flanges||
1-) Carbon steel
2-) Stainless steel AISI 316 –L or 304-L
4-) Customer Specification
|Flange drilling||: API Class 150, PN16, and Special|
|Flame element||: Stainless steel AISI 316 –L or 304-L|
|O-ring seal||: Nitrile, Special|
|Screen||: Stainless steel|
1-) Powder Coating, Colour RAL 9006
2-) Epoxy Paint, Colour RAL 9006
3-) Customer Specification
|ATEX cert||: Ex II 1/2 G IIB|
Design & Manufacturing Specifications
The size of the vent should be calculated in accordance with API Standard 2000 (ISO 28300) - Venting Atmospheric and Low-Pressure Storage Tanks or other international standards.
Data sheet, Model 340 In-line Deflagration Flame Arrester
- Elsewedy Electric PSP
Conducting business with ERGIL in the floating suction unit was a smooth process. Professional engineering - Read more
- Aegis Logistics Ltd. States
We feel happy to have been introduced to a team of professionals for our requirement of Internal - Read more
- IE Immanuel Engineering Pte.
While working with ERGIL, response has always been swift and guaranteed, whether it’s a working day or an official - Read more
- Tecnovent SL
We are glad to grow and expand together with ERGIL through the national territory and part South America. We - Read more